NFPA 58 Regulation: 2011 Compliance
Option 1, ESV Installation
NFPA 58 Sec. 188.8.131.52 (b)(2)c- containers over 4000 gallon WC for liquid inlet or withdrawal openings with a positive shut off valve located as close to the container as practical in combination with a excess flow valve in and retrofitted by July 1 2011 with an emergency shut off valve equipped for remote closure installed in line as close as practical to the existing positive shut off valve.
Compliance Page 1 | 2 | 3 | 4 | 5 | 6 | 7 | 8 | 9
Contact LPG Ventures and we can help you find the easiest, most economical solution for your equipment to meet NFPA 58 Regulations.